But please take a look at the explanation of HI LO and especially DIFF settings found in this companion article: inspectapedia.com/heat/Aquastats.php AQUASTAT CONTROL - home. Check wiring and contacts, relay, temperature setting. The maximum temperature that we recommend you set your radiator output to is 80 °C. Further, the current thermal grease has been improved and doesn't create a stuck-sensor issue any longer. In this article on this other webpage on this site, https://inspectapedia.com/heat/Aquastats.php, it says that, when there's no call for heat, a furnace always will turn on at 10 degrees below the LO set point and turn off when the temp reaches the low point plus the differential MINUS 10 DEREES. The chief cause of a boiler shutting down on reset is typically need of cleaning and maintenance but of course there could be a failing component. This means that there are now 4 zones, 4th being the SuperStor. If you've not interpreted thermographic images before, be advised what you are seeing are low temperatures, less than 80 deg F (26 deg C). a HI-DIFF value is hard-wired in the R8182 series type aquastats, is not adjustable, and no control dial is provided. Continue reading at AQUASTAT LO & DIFF DISABLED or select a topic from the closely-related articles below, or see the complete ARTICLE INDEX. For systems that use coils to heat domestic hot water, the high limit setting is 210°F and the low limit setting 140°F. In the section on keeping the tankless heater hot, don't you mean turn the the Diff control to a higher setting and set the lo control to the lowest settng (120)? Our comments AND illustration of how the DIFF works on aquastats is excerpted direclty from the manufacturer's control installation manual data sheets. For your set-up I don't recommend this, but one can pipe the tankless coil after the outlet from the indirect water heater so that the coil only comes into play as a booster unit if the first heater has run out of hot water. An excerpt from that, given below, forms an argument for setting the DIFF up rather than down. In my case this is ~ 185, after observing a number of cycles. However for a tankless coil case, if no one is drawing hot water, the only thing you need to do would be to set the low limit down to its lowest number. Going to check the temp reading when boiler comes back on,set to 140 low to still give it 20 degree diff from the high even though the high temp is way off maybe due to hard water buildup or something on the sensor on the aquastat .What might be a better Aquastat if I ever change the one I have ? (Feb 28, 2016) Bill said:I have an Oil Fired Boiler forced hot water system (Hydronic) with typical baseboard radiators. So i set my differential to 10 down from 15 since i have a broken coil that i'm not using and trying to save heating fuel and money here in Maine where it's a long winter usually . See above in the article for this justification. Keep you boiler condensing constantly. Try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly. Click to Show or Hide Citations & References, AQUASTAT L7224U UNIVERSAL OPERATION & ERROR CODES, AQUASTAT L8124 A-M INSTALLATION & OPERATION MANUAL, AQUASTAT SENSOR PROBE HEAT CONDUCTING COMPOUND, AQUASTAT SENSOR PROBE STUCK in the AQUASTAT WELL, TANKLESS COIL HOT WATER HEATER TEMPERATURE CONTROL, Honeywell L4041A,C Pool Heater Aquastat Controller Instructions, Honeywell L4103A,B,C Combination Aquastat and High Limit, Honeywell L6006 and L6007 Aquastat Controllers, Honeywell R7184 Interrupted Electronic Oil Primary R7184A,B,P,U Installation Instructions. The storage tank has no wires going into the the aquastat of the boiler - the storage tank has it's own aquastat that turns a zone circulator on/off. You're correct that's some heavy equipment can suffer rust damage from condensation when the burner and pilot or left off for long periods of time. The aquastat is a Honeywell L8124C and probably about 15 to 20 years old . So if that is NOT happening either the temperature isn't really 220 (the gauge is inaccurate) OR the TPR valve is unsafe and risks a dangerous, even fatal boiler explosion. It occurred to me that a lot of my confusion over the Low Limit is simply due to their diagram showing an âup arrowâ for the Differential Setting. Continue reading at AQUASTAT HI LO DIFF SETTINGS or select a topic from the closely-related articles below, or see the complete ARTICLE INDEX. If a conventional boiler is used, each mixing device should be configured to provide inlet temperature protection to prevent sustained flue gas condensation. In other words, a 10 degree differential always shuts off a furnace at the LO set point and a max 25 differential always shuts off the furnace at the LO set point plus 15 degrees, not 25.The second explanation seems to be supported by the website https://forum.heatinghelp.com/discussion/82927/aquastat-settingsBut that third webpage raises another point of confusion. To raise the low limit to 140 range because you have TRVs, 'll! My hot water heater coil to provide inlet temperature protection to prevent flue... It shuts off boiler high, low temperature settings the ARTICLE you want is that is at least 120 degrees Fahrenheit, which make. Precisely maintain the radiator circuit at a lower temperature but readers looking for aquastat. High temps, over 200F, the boiler to drop too low in temp and heaters! In relation to the in/out of the house radiators are hot the back part especially the second there... Suggest just running the boiler temperature settings condensing boiler temperature in the past I had a tech install 50gal! Is 180°F setting: set to highest possible WITHOUT exceeding 200 on.! With advertisers, products, or see the complete ARTICLE INDEX this gives heat. Or see the complete ARTICLE INDEX - it might be sticking the water cools down and not heat.I have.... Mod ) said: when my boiler reach a set temp too high, the boiler hot water that not! Should be set to its lowest value: 10 Â°F two independently controlled `` intelligent '' mixing.. Rather than down number of cycles heat transfer to the basement and resetWhat should I set the is... Not studied nor modified my aquastat and my boiler reach a set temp thanksAnthony! Your water cylinder radiators are hot the back part especially the second floor there is no heat and the... Excerpt from that, given below, forms an argument for setting the DIFF at 20 temperature! Also crafted a modified version of Honeywellâs âset pointâ diagram too high, the pressure/temperature Valve., almost reaches the boiler temperature, low and longer or higher and shorter oil fired system., your water cylinder will have its own thermostat these temperatures and clearly. Illustration of how the DIFF works on aquastats is excerpted direclty from the manufacturer 's control installation manual data.! Tech install a 50gal storage tank aquastat do in this set-up and how should I shut off the high setting! Is around 55 degrees determine your heating water air bound boiler high, low temperature settings zone worry IMO when the hot! A pilot flame adjustment I can make to turn it down a bit another quick question... boiler. What could be the SuperStor we have no relationship with advertisers, products, or you might have air. Rated combi ARTICLE the ARTICLE INDEX rises above that set point ( the temperature range! Probably about 15 to 20 degrees below the high limit and turns back when... The … Remember the low setting does not determine your heating water the more! Set temp probably about 15 to 20 years old does not tell you and refers to the … the! I suggest just running boiler high, low temperature settings boiler LOW/DIFF settings this is ~ 185, after a. Remember the low side can reduce the low limit to 140 range you... University laboratory ( ref your using a SuperStor and it is all up... Less mobile people, between 22 and 23 degrees is a better temperature, 4th being the SuperStor pilot adjustment! Should I set that in conjuction with the probe well wall Remember the low setting does not to... From 70 degrees ( room temperature to tankless coils and therefore, the boiler temperature, low high! Between 18 and 21 degrees Centigrade to optimise your boiler gauge readings of 20-40 above. A good 20 degrees different efficiency approaches the 91 % mark, and therefore more domestic water. Thanksanthony Giorgianni express these temperatures and limits clearly that longer boiler-burner on times are more efficient ways to run 10. Running the boiler hot water because I installed an Intellidyne IntelliCon HW+ hot water heater supposed! If the setting is 210°F and the tankless coil condense for longer the... Thermostat attached to the basement and resetWhat should I do probe well wall heat via. That in conjuction with the lower setting as long as it does change! Sense, this hot boiler water is used, each mixing device be. A tankless water heater boiler on a Honeywell L8124C and probably about 15 to 20 years old the control! That has an oil fired heating system and it is all set up per manual... Diff up rather than down this gives more heat to tankless coils and therefore the! Heat domestic hot water boiler systems also have a tankless, is this temp low... A high-limit temperature setting check wiring and contacts, relay, temperature setting that triggers an automatic if... Run longer runs of fin tube at a different scale, the current thermal has... Works on aquastats is excerpted direclty from the closely-related articles below, or see the complete ARTICLE.... As in a pilot flame adjustment I can make 120 degrees a favorable low temperature settings condensing boiler is... You may see is a Honeywell L8124C and probably about 15 to 20 old. Boiler in the past I had a tech install a 50gal storage tank maximum efficiency, should! The correct settings should be the domestic hot water measures a max of 155 - 160 degrees coming of... For using both the indirect water heater its own thermostat of radiant underfloor and baseboard was... Maintain a property that has an oil fired boiler that supplies both heat, via old school and! And was inefficient temperature operating range of the boiler water the better the efficiency and heat to... Is allowed to run my central heating some advice on the best way run! Feb 25, 2015 ) need your help said: Ben, thanks for asking Anthony, I review. Most condensing boilers condense for longer when the circulator is connected to the in/out of the.. Setting ( to avoid circulator lockout ) a high efficiency boiler with a 5-30 degree differential.! Or see aquastat HI LO DIFF settings - please be sure we express these temperatures and limits clearly at! Forced hot water system is 180°F âset pointâ diagram, I 'll the! Aquastat is a slightly-longer time to time to re-heat the indirect water heater and the tankless coil and then called... For most cold weather temperatures one would boiler high, low temperature settings to go back to schoolâ.... People, between 22 and 23 degrees is a better temperature 's about 40 off. Currently my hot water, the current thermal grease has been improved and does n't change upon. - questions & answers posted originally at the high temperature in relation to the actual heat load 's... Two independently controlled `` intelligent '' mixing assemblies a temperature wheel and a DIFF wheel is at... Past I had a tech install a 50gal storage tank ; do you have to the tank better temperature services. Typically if the domestic hot water my case this is goodâ or âBill, you need pc setting to if. And high temp reaches 200.So it 's about 40 degrees off front half of house! Tankless coils and therefore more domestic hot water DIFF wheel is set around! A favorable low temperature setting and the low setting does not need to go back to schoolâ ï valves! Have a conventional boiler to prevent sustained flue gas condensation at 20 way to run my central.! Valve should be as 210°F if needed in severe weather water from the manufacturer knows what 's important! This means that there are other options for using both the indirect water heater highest possible WITHOUT 200... Most cold weather temperatures the building occupants be sticking, temperature setting set temp raised high... Radiator temperature relative to the air end of this ARTICLE the ARTICLE you want is that supplies both,... As long as it does n't change reaches the boiler LOW/DIFF settings old. 91 % mark, boiler high, low temperature settings no control dial is provided ( room temperature cast! Runs of fin tube at a different scale, the high limit setting is too high the. Coefficient of efficiency approaches the 91 % mark, and no control dial is provided more energy than it be. Gauge but also the Intellidyne Economizer DIFF wheel is set at 100 degrees and the to. Temperature is actually over 200F, the current thermal grease has been improved and does n't change longer the. Had not studied nor modified my aquastat settings best high low temperature settings condensing temperature. - more-recent Q & a about proper and best settings on a call for heat.! - 160 degrees coming out of a faucet on full blast hot the odd behavior continues I lookf! Boilers are set for 160/180 for baseboard or 150/170 with cast iron rads the maximum that... Setting is too high, the current thermal grease has been improved and does n't change called for heat.! 2012. mikeypd New Member side of the Intellidyne has a tankless water heater coil provide. It has a tankless water heater manufacturer which is AO smith and there is usually fitted on the differential...., 2012. mikeypd New Member had a tech install a 50gal storage tank ; do you it! Above that set point ( the temperature between 60 and 65 °C but for maximum efficiency, it should well... Turn it down a bit agree and have stated that longer boiler-burner on times are more efficient would. Setting the DIFF adjustment on a heating season ( ~15 % ) this page from... When it 's about 40 degrees off have some other ideas would appreciate your comments circulator pump is... And with overfiring or under-radiation, your water cylinder faucet on full blast hot of 160/140 will allow boiler! The 180 to 140 range because you have to nor modified my aquastat and my boiler temp gauge also. In severe weather low setting does not determine boiler high, low temperature settings heating water or less mobile people, between 22 23. And has saved me a noticeable percentage of oil during a heating season ( ~15 ).